100% Original Factory KYN61-40.5 Metal Armored Removable Switchgear Export to Nigeria
Exterior and dimensions
Our company has been focusing on brand strategy. Customers' satisfaction is our best advertising. We also supply OEM service for 100% Original Factory KYN61-40.5 Metal Armored Removable Switchgear Export to Nigeria, We appreciate your enquiry and it's our honor to work with every friend worldwide.
KYN61-40.5 is the 35KV class switchgear that is developed by bringing in the foreign technology. It is in line with GB3906, IEC-298, DL404 and other standards. It is applicable to the system of three-phase AC 50Hz, rated voltage 40.5KV for the use of power plant area, substation and large industrial mining enterprises to accept and distribute the electric power. It can control, protect and detect the line.
Go to http://www.southlandelectrical.com/itemdesc.asp?ic=FAL32080-NS to shop online for this Square D FAL32080, 80 Amp, 240 Volt, 3 Pole Circuit Breaker. Southland Electrical is a world class leader in Power Distribution and Low Voltage Motor Control. For over 30 years we have been buying and selling New, New Surplus and Reconditioned industrial electrical equipment.
Disclaimer: This video is to show the way I did the job of upgrading my 10/3 feeder wire. I am not showing the way all the experts watching would do it. I am a licensed aircraft avionics (electrician) not a home electrician:I did not cut a long opening in the drywall. This sub-panel was inspected by an electrical underwriter back in 1985. Now I am wiring my new workshop with an existing sub-panel I had installed back in 1985. I am a licensed aircraft technician and was allowed by the town code board to wire my own one family house wiring, including connecting to the incoming power company wiring that terminated on a pole connected to my house, this was back in 1985, I do not think that is allowed anymore.Now I am updating the size to 10/3 coming from the sub-panel to the underground UV cable I had buried back in 1985. The two 30 amp switches I have been using, although renewed, could be eliminated and just use the sub panel circuit breakers when your not using shed power, also I am installing an 8 foot copper rod, pounded into the ground and connected to the shed box neutral bar using unshielded solid # 4 copper wire with the required rod clamp. The main house neutral bar is also connected to a #4 solid copper ground wire unbroken to the pipe below the house’s main water shut off valve and continues out of the house and connected to an 8 foot copper rod with heavy required clamp.This gets pounded below the dirt close to the foundation. Over 616 HD Video