12 Years Factory wholesale Miniature circuit breaker-FTM9-100 for Seattle Factory
Exterior and dimensions
owing to good service, a variety of high quality products, competitive prices and efficient delivery, we enjoy a good reputation among our customers. We are an energetic company with wide market for 12 Years Factory wholesale Miniature circuit breaker-FTM9-100 for Seattle Factory, We welcome new and old customers from all walks of life to contact us for future business relationships and mutual success!
|Rated current (A):||63,80,100|
|Rated voltage (V)||230,400|
|Rated impulse withstand voltage Uimp(KV):||4|
|Operating cycle times:||/hour||120|
|Conventional non-tripping current||t≤1h(In=63A) t≤2h(In>63A)|
|Conventionaltripping current:||1.45In||t<1h(In=63A) t<2h(In>63A)|
|Instantaneous tripping type:||D|
|Instantaneous non-tripping current:||t≤0.1s||10In|
|Instantaneous tripping current:||t<0.1s||20In|
|Connection Wire ㎜²:||Min/Max||16/50|
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/F2025,22-14510.aspx
Stock # 22-14510, CUTLER HAMMER, Circuit Breaker, Catalog No. F2025, Frame Amps 100, Trip Amps 25, 2 Poles, 600 Volts
Reconditioned Circuit Breakers
The F2025 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The F2025 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the F2025. These services far exceed the routine reconditioning of the F2025 performed by many circuit breaker vendors and resellers. MIDWEST certifies the F2025 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the F2025 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus F2025 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus F2025 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209
In this Session you will learn about the Importance of CADD Designing in Electrical Field.