13 Years Factory wholesale Automatic Transfer Switching Equipment-FTQ2 Supply to Germany
Exterior and dimensions
Our goal is to satisfy our customers by offering golden service, good price and high quality for 13 Years Factory wholesale Automatic Transfer Switching Equipment-FTQ2 Supply to Germany, We sincerely welcome overseas customers to consult for the long-term cooperation and the mutual development.We strongly believe that we can do better and better.
|Rated operational voltage Ue(V):||AC400V/50HZ|
|Rated operational current Ie(A):||20,25,32,40,50,63,80,100,125,160,180,200,225,315,350,400,500,630|
|Rated insulation voltage Ui(V):||690V|
|Operating position:||Normal power switch-on, backup power switch-on, Normal power& backup power switch-off|
|Rated controller Operating supply voltage:||AC220V|
|Under-voltage:||Adjustable from 160-200v,factory defaults:170V|
|Over-voltage:||Adjustable from 240-290V,factory defaults:270V|
|Operation Mode:||R:automatic change recovery,S:automatic change but not automatic recovery,F:Generator type|
|Switch-off delay time:||Adjustable from 0-180s,factory defaults:2s|
|Switch-on delay time:||Adjustable from 0-180s,factory defaults:2s|
The most effective and easiest way to remove mastic or thinset from a concrete floor after the tiles have been removed. Link to my other video on how to remove tile flooring which is the 1st step: http://www.youtube.com/watch?v=z-OMxMe589c
How to tile and grout a floor: http://www.youtube.com/watch?v=-Ws0Lc1hiKc Visit my channel for more DIY videos http://www.youtube.com/user/djlattas
This circuit breaker was extremely loose, which means it may not be making proper contact with the bus bar. The fix is to have the circuit breaker replaced.