15 Years Factory MNS Low Voltage Withdrawable Switchgear to Nigeria Factories
Exterior and dimensions
We aim to find out quality disfigurement from the production and supply the best service to domestic and overseas customers wholeheartedly for 15 Years Factory MNS Low Voltage Withdrawable Switchgear to Nigeria Factories, "Passion, Honesty, Sound service, Keen cooperation and Development" are our goals. We are here expecting friends all over the world!
MNS low-voltage withdrawable switchgear is suitable in three-phase, four-wire and three-phase five-wire power system with three-phase AC 50 or 60 Hz, rated voltage 660V, rated current ≤ 4000A , for the use of electricity power acceptance and distribution. It is widely used in power plants, substations, factories, mines, high-rise buildings of the power distribution center PC and motor control center MCC.
This product complies with GB7251.1-91, ZBK36001-89, IEC439-1 (1992) standard and passed CCC certificate:
An Arc Flash Presentation
Arc Flash Protection for Working on LV & HV Circuit Breakers
CATU Arc Flash Clothing Kits for Safe Electrical Switching Operations
Many arc flash incidents occur when personnel insert or remove (rack) circuit breakers from low or high voltage switchgear cubicles. Manual racking in and racking out circuit breakers poses potentially lethal arc flash exposure.
Assumptions and complacency are two of electrical safety’s worst enemies. If the following story hits uncomfortably close to home for you, it will have served its purpose.
In January 1993, two employees were killed and three were seriously injured by an electrical arc flash at a Texas power station.
The dead employee had racked-in a circuit breaker and sent the close command, but the breaker failed to close. With the breaker indicator showing that it was still open, the operator began racking-out the breaker to troubleshoot the problem with his supervisor looking on. Neither knew that the breaker had received the close command. The breaker had unlatched and begun to close, but the mechanical problem prevented it from completing the operation.
As a consequence, the operator attempted to rack out the breaker even as it was receiving a close command. When he was finally able to move the breaker, the mechanical bind was relieved and the breaker closed while it was partially racked-out. The result was an electrical arc flash and explosion that critically burned the operator and the supervisor and slammed them into the wall. Both were killed. The arc flash then travelled around a corner and burned three other workers. All of this carnage occurred within milliseconds.
Thorne & Derrick UK (tel 0191 4901547) are national distributors and worldwide exporters of LV-HV Cable Installation, Cable Jointing & Electrical Equipment – we service UK and global businesses involved in cable installations, cable jointing, substation and electrical construction at LV, 11kV, 33kV and EHV. T&D service utilities, power, construction, rail, mining, offshore, oil, gas, petrochemical and hazardous area industries.
For more products please visit www.cablejoints.co.uk
Arc Flash Clothing : http://www.cablejoints.co.uk/sub-product-details/arc-flash-clothing-ppe
Operation of a thermocouple Amplifier to connect a low-voltage thermocouple to a AD input on a micro controller.