16 Years manufacturer Miniature Circuit Breaker FTB1 to Barbados Manufacturer
Exterior and dimensions
Sticking to the belief of "Creating products of high quality and making friends with people from all over the world", we always put the interest of customers in the first place for 16 Years manufacturer Miniature Circuit Breaker FTB1 to Barbados Manufacturer, We appreciate your enquiry and it's our honor to work with every friend worldwide.
|Auxiliary contact||Auxiliary contact and alarm contact||Shunt release||Shunt release and auxiliary contact||Under voltage release||Over voltage release||Busbar mounting base||Motor-driven operation|
Under normal condition, the working principle of main thermostic bimetal in FTB1 SMCB is the same to the usual circuit breakers, it is used for overload tripping. when there is a short-circuit on a branch circuit breaker, the magnet core in the main current path would tilt the moving contact away from the fixed contact to break the circuit,thus producing the electric arc, and limiting the short-circuit current effectively.
In the maintime,the short-circuit current flow to the supplementary current path, a selective resistor and a selective bimetal are connected in series of the supplementary curret path, limiting the short-circuit current to a few hundred amps.
When the downstream circuit-breaker has tripped because of a short-circuit, the contact tips reclose automatically through a simple spring-type system,ensuring other unaffected branch circuits continue in operation.If a short-circuit occur between the FTB1 and the downstream circuit-breaker, another bimetal release enables short-time delayed tripping,ensuring the contact tips remain in the open position enabling isolating.
Scope of use
It is primarily used in critical installations,for instance, office buiding, laboratory, theatre, museum, hotel, shopping mall, telecommunication, coal mine and shipping, chemical industry and metallurgy, industrial plants,medical and health care, bank and securities exchange,airport, underground express way, military establishment and similar loads that requires non-interrupted and reliable power supply.
|Test||Tripping characteristic||Conventional non-tripping current||Conventional tripping current||Initial status||Tripping time|
|a b||E E||1.05In||1.2In||Cold statusRight after test 1||≧2h﹤2h|
|Test||Tripping characteristic||Delayed tripping current||short-time delayed tripping current||Initial status||Tripping time|
|c||E||5In||Cold status||0.05s<t<5s(In≦32A) 0.05s<t<10s(In>32A)|
The FTB1 series operates selectively with respect to the combination with MCBs
|MCB(B,C characteristic) FTB1(Characteristic E)|
Note: T represents total selectivity
Exterior and dimensions
I have owned this electric mower by Greenworks for about eight to nine months. It recently broke down and would not start. It resets the breaker every time I try to get it to turn on. So I found some vids on youtube on some possibilities and one guy hit it on the nail with the rectifier. In this video I talk about doing this repair in hopes that it could help someone else out there with the same problem.
If you are going to do this repair, you might as well add some thermal paste. See my video on adding thermal paste here :
Model number of rectifier is KBPC2504
Greenworks 20 inch corded mower
AmazonBasics Outdoor Extension Cord 50 feet 16 gauge
Coleman Cable 02409 14/3 SJTW Vinyl Outdoor Extension Cord, Red, 100-Foot 14 gauge