20 Years manufacturer Miniature circuit breaker-FTB10LE for Holland Factories
Exterior and dimensions
Our company promises all users of the first-class products and the most satisfying post-sale service. We warmly welcome our regular and new customers to join us for 20 Years manufacturer Miniature circuit breaker-FTB10LE for Holland Factories, We sincerely welcome you come to visit us. Hope we have good cooperation in the future.
|Rated current (A)：||6,10,16,20,25,32,40|
|Rated operational voltage(V):||230|
|Rated residual operating current:A/AC:||30|
|Breaking Time ms :||I△=I△n||≤100|
|Mechanical and electrical life:||10000|
|Conventional non-tripping current:||t≤1h|
|Conventional tripping current:||t≤1h|
|Instantaneous tripping types:||C|
|Instantaneous non-tripping current:||5In|
|Instantaneous tripping current:||10In|
How to Replace a Breaker (Residential Panel)
This is extremely simple, and not to be feared, but rather, respected. Just make sure first order of business is to flip the main breaker so the whole panel is dead. Even still, I make sure to wear rubber soled shoes and use rubber/plastic handled tools. You can just never be too safe with electrical.
Kill the main
Disconnect wires from old breaker
Pull it out
Plug wires into new breaker
Push it in
It really is that simple. Takes 3 minutes to explain and about 30 seconds to do.
Now as I mentioned this breaker was actually a sort of GFCI breaker, so it’s like a breaker within a breaker. I was replacing it because it tripped but when I went to reset it, it wouldn’t stay reset. So because of it’s internal grounding mechanism, it carries the extra neutral wire that a standard breaker does not.