2017 New Style Automatic Transfer Switching Equipment-FTQ2 to Factories
Exterior and dimensions
Our advantages are lower prices,dynamic sales team,specialized QC,strong factories,high quality products and services for 2017 New Style Automatic Transfer Switching Equipment-FTQ2 to Factories, We are glad that we are steadily growing with the active and long term support of our satisfied customers !
|Rated operational voltage Ue(V):||AC400V/50HZ|
|Rated operational current Ie(A):||20,25,32,40,50,63,80,100,125,160,180,200,225,315,350,400,500,630|
|Rated insulation voltage Ui(V):||690V|
|Operating position:||Normal power switch-on, backup power switch-on, Normal power& backup power switch-off|
|Rated controller Operating supply voltage:||AC220V|
|Under-voltage:||Adjustable from 160-200v,factory defaults:170V|
|Over-voltage:||Adjustable from 240-290V,factory defaults:270V|
|Operation Mode:||R:automatic change recovery,S:automatic change but not automatic recovery,F:Generator type|
|Switch-off delay time:||Adjustable from 0-180s,factory defaults:2s|
|Switch-on delay time:||Adjustable from 0-180s,factory defaults:2s|
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/KA36110,22-13399.aspx
Stock # 22-13399, SQUARE D, Circuit Breaker, Catalog No. KA36110, Frame Amps 250, Trip Amps 110, 3 Poles, 600 Volts,
Reconditioned Circuit Breakers
The KA36110 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The KA36110 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the KA36110. These services far exceed the routine reconditioning of the KA36110 performed by many circuit breaker vendors and resellers. MIDWEST certifies the KA36110 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the KA36110 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus KA36110 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus KA36110 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209
Short video made by Aaron MacRaighne, Matt Barr and Fiona Meade – covering eddy currents, magnetic braking and Lenz’s Law