2017 New Style Automatic Transfer Switching Equipment-FTQ2E to Hungary Factories
Exterior and dimensions
Our company sticks to the principle of "Quality is the life of the company, and reputation is the soul of it" for 2017 New Style Automatic Transfer Switching Equipment-FTQ2E to Hungary Factories, Your inquiry will be highly welcomed and a win-win prosperous development are what we are expecting.
|Body switch||FTB2-63 MCB Series|
|Rated voltage (V)：||AC 400(4P/3P); AC 230V(2P)/50HZ|
|Rated insulation voltage:||440|
|Rated impulse withstand voltage Uimp(KV):||4|
|Rated breaking Capacity：||6.5|
|Mechanical and electrical life:||electric||6000|
|Operating position:||Normally on,backup on,Normal and backup off|
|Operating transfer time:||≤1.5|
switch automaticly in condition of phase loss, pressure loss ,undervoltage and other power failure,
automatic change and automatic recovery ,automatic change and non automatic recovery,fire fighting
joint control, Manual/automatic adjustion,power/power on/tripping indication,fault alarm
|Controller Operating Voltage:||AC230V/50Hz|
|Undervoltage conversion value:||AC175V(±5)|
|Undervoltage return value:||AC190V(±5)|
|Conversion Delay(normal to backup):||0S-60S adjustable,factory default setting:5S|
|Return Delay（normal to backup:||0S-60S adjustable,factory default setting:5S|
|Size（L×W×H）mm:||248 × 125×121|
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/TEY360,22-11279.aspx
Stock # 22-11279, GENERAL ELECTRIC, Circuit Breaker, Catalog No. TEY360, Frame Amps 100, Trip Amps 60, 3 Poles, 480 Volts,
Reconditioned Circuit Breakers
The TEY360 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The TEY360 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the TEY360. These services far exceed the routine reconditioning of the TEY360 performed by many circuit breaker vendors and resellers. MIDWEST certifies the TEY360 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the TEY360 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus TEY360 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus TEY360 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209