2017 New Style DC miniature circuit breaker-FTBD to United Arab emirates Manufacturer
Exterior and dimensions
No matter new customer or old customer, We believe in long term and trusted relationship for 2017 New Style DC miniature circuit breaker-FTBD to United Arab emirates Manufacturer, We believe that a passionate, innovative and well-trained team will be able to establish good and mutually beneficial business relationships with you soon. Please feel free to contact us for more details.
|Model||FTBD DC miniature circuit-breaker|
|Number of poles||IP||2P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V)||125/250||250/500|
|Rated current (A)||1,2,3,4|
|Rated ultimate short-circuit breaking capacity(KA)||6.5|
|Rated current (A)||6,10,16,20,25,32,40,50,63|
|Rated ultimate short-circuit breaking capacity(KA)||20/10||20/10|
|Rated impulse withstand voltage Uimp(KV)||4|
|Mechanical and electrical life:||20000|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm2, Cross-section of busbar from 0.8-2mm2|
|Ambient temperature (°C)||-25°C ~ +45°|
|Relative air humidity||no more than 95%|
|Installation condition||Used in place without obvious shock and vibration|
Exterior and dimensions
|Number of poles||1P 2P|
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/F2010,22-1404.aspx
Stock # 22-1404, WESTINGHOUSE, Circuit Breaker, Catalog No. F2010, Frame Amps 100, Trip Amps 10, 2 Poles, 600 Volts
Reconditioned Circuit Breakers
The F2010 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The F2010 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the F2010. These services far exceed the routine reconditioning of the F2010 performed by many circuit breaker vendors and resellers. MIDWEST certifies the F2010 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the F2010 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus F2010 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus F2010 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209
http://www.sparkyuonline.com (Basic Electrical Wiring) Here is a short video explaining how to wire a single pole light switch during the rough in process of rewiring a residential home.
You have power coming in and you have a switch leg going out to the light. I also explain that you should leave about 8″ of wire during make to attch safely to the light switch.
Some people make these wires so short it makes it difficult to wire the light switch.