26 Years Factory Automatic Transfer Switching Equipment-FTQ2 to Johor Manufacturers
Exterior and dimensions
"Quality first, Honesty as base, Sincere service and mutual profit" is our idea, in order to develop continuously and pursue the excellence for 26 Years Factory Automatic Transfer Switching Equipment-FTQ2 to Johor Manufacturers, We sincerely welcome overseas customers to consult for the long-term cooperation and the mutual development.
|Rated operational voltage Ue(V):||AC400V/50HZ|
|Rated operational current Ie(A):||20,25,32,40,50,63,80,100,125,160,180,200,225,315,350,400,500,630|
|Rated insulation voltage Ui(V):||690V|
|Operating position:||Normal power switch-on, backup power switch-on, Normal power& backup power switch-off|
|Rated controller Operating supply voltage:||AC220V|
|Under-voltage:||Adjustable from 160-200v,factory defaults:170V|
|Over-voltage:||Adjustable from 240-290V,factory defaults:270V|
|Operation Mode:||R:automatic change recovery,S:automatic change but not automatic recovery,F:Generator type|
|Switch-off delay time:||Adjustable from 0-180s,factory defaults:2s|
|Switch-on delay time:||Adjustable from 0-180s,factory defaults:2s|
This video will show how to check the voltages fdor the spa and GFCI voltage check. *** CAUTION *** High Voltages which can cause serious injuries and death. This video is intended for Electricians and not Homeowners. This video is a part of the Balboa technical series.
For information on replacement systems, visit http://www.balboawatergroup.com/Retrofit-Kits
© Balboa Water Group. All rights reserved.
Disclaimer: This video is to show the way I did the job of upgrading my 10/3 feeder wire. I am not showing the way all the experts watching would do it. I am a licensed aircraft avionics (electrician) not a home electrician:I did not cut a long opening in the drywall. This sub-panel was inspected by an electrical underwriter back in 1985. Now I am wiring my new workshop with an existing sub-panel I had installed back in 1985. I am a licensed aircraft technician and was allowed by the town code board to wire my own one family house wiring, including connecting to the incoming power company wiring that terminated on a pole connected to my house, this was back in 1985, I do not think that is allowed anymore.Now I am updating the size to 10/3 coming from the sub-panel to the underground UV cable I had buried back in 1985. The two 30 amp switches I have been using, although renewed, could be eliminated and just use the sub panel circuit breakers when your not using shed power, also I am installing an 8 foot copper rod, pounded into the ground and connected to the shed box neutral bar using unshielded solid # 4 copper wire with the required rod clamp. The main house neutral bar is also connected to a #4 solid copper ground wire unbroken to the pipe below the house’s main water shut off valve and continues out of the house and connected to an 8 foot copper rod with heavy required clamp.This gets pounded below the dirt close to the foundation. Over 616 HD Video