26 Years Factory Automatic transfer switching equipment-FTQ3 to Greenland Factory
Exterior and dimensions
With a sound business credit, excellent after-sales service and modern manufacturing facilities, we have earned an excellent reputation among our customers across the world for 26 Years Factory Automatic transfer switching equipment-FTQ3 to Greenland Factory, welcomes all overseas friends and merchants to establish collaboration with us. We will provide you with honest, high quality and efficient service to meet your requirements.
|Rated current (A)Ie:||16,20,25,32,40,50,63||63,80,100,125||125,160,200,225,250||250,300,315,350,400||400,500,630,800|
|Main function:||Mainly used for power circuit monitoring.When the normal power supply is in the event of failure,it will transfer the power supply
from normal power to backup power supply and finish the switching the circuit system.
|Rated voltage (V):||AC 400V|
|Rated insulation voltage:||800|
|Rated impulse withstand voltage Uimp(KV):||8|
|Connection and breaking capacity:||10Ie||6Ie|
|Status indication:||Normal power/backup power on-off,Fault display,Fire linkage display,Normal power/backup power voltage.|
|Connection mode:||Front connection plate|
|Minimum transfer time||50||50||75||75||1200|
|Operation cycle time(time/hour)||120|
Shawn Warman talks about how to change fuses on the Peterbilt 389 Model.
Visit Peterbilt Atlantic anytime at: http://www.peterbiltatlantic.com
An update to our original video for the ankle breaker badge and how to get it. More info has surfaced and we now have a clear method! Fast shout to the originator of this technique Manman GrindHard. Link to his YT is below.