27 Years Factory Miniature circuit breaker-FTB10 for Oman Manufacturers
Exterior and dimensions
The very rich projects management experiences and one to one service model make the high importance of business communication and our easy understanding of your expectations for 27 Years Factory Miniature circuit breaker-FTB10 for Oman Manufacturers, We warmly welcome business partners from all walks of life, expect to establish friendly and cooperative business contact with you and achieve a win-win goal.
|Rated current (A):||6,10,16,20,25,32,40|
|Rated voltage (V):||230|
|Rated impulse withstand voltage Uimp(KV):||4|
|Operating cycle times||/hour||240|
|Conventional non-tripping current:||1.13In||t≤1h|
|Instantaneous tripping type:||C|
|Instantaneous non-tripping current:||t≤0.1s||5In|
|Instantaneous tripping current:||t<0.1s||10In|
|Connection Wire ㎜²:||Min/Max||1/10|
This device is called an isolator. It’s a mechanical disconnect that opens and closes a 500,000 volt electrical transmission line at the El Dorado electrical substation near Boulder City, Nevada. Another device called a switcher is supposed to open the circuit first, then the isolator opens to physically disconnect the circuit. The switcher has had a history of one of the three phases failing to open. When this happens, the isolator opens with one phase still energized. Since the isolator isn’t designed to open hot, there’s no arc suppression, and the result is quite spectacular. Because of the history of periodic failures when the switcher has been opened, a video camera had been set up to try and record the event should it happen again. They were in luck and caught it. The arc ends when an upstream circuit breaker is opened. Full credit goes to Neil Brady who captured this amazing sight. The “wow” at the end of the video says it all.