Cheapest Factory FTHN-12 (XGN15-12) Metal Closed Box ing High Voltage Switchgear to Poland Factory
Exterior and dimensions
We rely upon strategic thinking, constant modernisation in all segments, technological advances and of course upon our employees that directly participate in our success for Cheapest Factory FTHN-12 (XGN15-12) Metal Closed Box ing High Voltage Switchgear to Poland Factory, With superb service and quality, and an enterprise of foreign trade featuring validity and competitiveness, that will be trusted and welcomed by its clients and creates happiness to its employees.
FTHN-12 Indoor exchange metal closed box ring high voltage switchgear is Complete sets of power distribution equipment with 3.6 ~ 12Kv, three-phase, AC 50Hz. It is widely used in the power distribution system of construction and transformation of urban power grids also used in the power supply system of the industrial and mining enterprises, high-rise buildings, residential quarters, hospitals, schools, parks etc for the use of the power acceptance and distribution.
Mainly used for ring network power supply system, for the use of power acceptance and distribution.
Mainly used for ring network power supply and terminal power supply, also suitable for installing into the assembly substation.
This product complies with GB3804-1990, GB3906-2006, GB16926-1997, GB / T11022-1999, GB15166.2-1994, GB1985-1989, GB3309-1989, IEC420-1990 and other standards, and passed all type of test.
Operating environmental conditions
A) Ambient temperature
Maximum temperature: + 40 ℃
Minimum temperature: -15 ℃
Daily average: ≤35 ℃
B) Ambient humidity
Daily average relative humidity: ≤ 95%
Monthly average relative humidity: ≤90%
Daily average vapor pressure: ≤2.2X10-3 Mpa
C) Altitude: no more than 1000m;
D) earthquake intensity does not exceed 8 degrees;
E) Operating place without water dripping, no flammable and explosive hazards, no chemical corrosion of gas and no severe vibration.
This is only a temporary fix to an emergency situation. Always call a licensed electrician, the electrical panel box must be replaced. Make sure a permit is pulled and the local utility company is called. Do not attempt this unless you are qualified to do so.
Jones Air Conditioning
3920 Progress Ave Suite A5
Naples, FL 34104
Unibis™ MCBs are one of the latest introductions in the ElfaPlus range and are developed to reduce the size of the distribution board to the minimum.
For more details look at http://www.gepowercontrols.com/eu