Cheapest Price Miniature circuit breaker-FTB2LE for Montpellier Manufacturers
Exterior and dimensions
With our rich experience and considerate services, we have been recognized as a reliable supplier for many international buyers for Cheapest Price Miniature circuit breaker-FTB2LE for Montpellier Manufacturers, "Quality first, Price lowest, Service best" is the spirit of our company. We sincerely welcome you to visit our company and negotiate mutual business!
|Model||FTB2LE Miniature circuit-breaker|
|Number of poles||IP+N,2P,3P,3P+N,4P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V) AC||230/400|
|Rated current (A)||C
|6, 10, 16, 20, 25, 32, 40, 50, 63
|Rated residual operating current(mA)||AC A||30
|Rated residual non-operating current(mA)||AC
|Residual current breaking time||30mA≦0.1s 250mA≦0.04s|
|Max. breaking time(s)||0.1|
|Rated short-circuit breaking capacity(KA)||6.5|
|Rated residual current breaking capacity(KA)||4.5|
|Mechanical & electrical life:||20,000 operations|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm², Cross-section of busbar from 0.8-2mm²,reversibility of connections|
|Tightening torque||2 Nm|
|Ambient temperature (°C)||- 5°C ~ +40°C|
|Relative air humidity||no more than 95%|
|Installation condition||Used in place without obvious shock and vibration|
|Weight (g)||340 420 530 630 710|
Exterior and dimensions
|Number of poles||Width（mm）||Modules|
|1 / 2||54||3|
|2 / 2||72||4|
|3 / 3||100||5.5|
|3 / 4||112.5||6.25|
|4 / 4||130.5||7.25|
via YouTube Capture.
http://albanyelectric.biz/ (229) 432-7345
GFCIs are designed to prevent electrical shock by breaking the circuit when there is a difference in currents in the hot and neutral wires.
Receptacles on the outside of your house and near sinks have special protection known as GFCI. If you lose your power, find the GFCI receptacle and reset the button.
If your GFCI has tripped, push the “Reset” button located on the GFCI receptacle to assure normal operation.
Plug a lamp into the GFCI receptacle and turn the lamp “ON.”
Push the “Test” button located on the GFI receptacle. The lamp should go “OFF.”
Push the “Reset” button. The lamp should turn “ON.”
If you don’t have any GFCI’s in your home, give Albany Electric a call today.
Contact us online or give us a call today!
This video relates to Albany Electric, the professional electrical services business located in Albany, GA whose electricians provide prompt & efficient services to residential and commercial customers in Albany, GA as well as the surrounding communities.