Chinese wholesale Miniature circuit breaker-FTB2LE to Canada Manufacturer
Exterior and dimensions
Assume full responsibility to meet all demands of our clients; achieve continuous advancements by promoting the growth of our clients; become the final permanent cooperative partner of clients and maximize the interests of clients for Chinese wholesale Miniature circuit breaker-FTB2LE to Canada Manufacturer, Standing still today and looking into the future, we sincerely welcome customers all over the world to cooperate with us.
|Model||FTB2LE Miniature circuit-breaker|
|Number of poles||IP+N,2P,3P,3P+N,4P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V) AC||230/400|
|Rated current (A)||C
|6, 10, 16, 20, 25, 32, 40, 50, 63
|Rated residual operating current(mA)||AC A||30
|Rated residual non-operating current(mA)||AC
|Residual current breaking time||30mA≦0.1s 250mA≦0.04s|
|Max. breaking time(s)||0.1|
|Rated short-circuit breaking capacity(KA)||6.5|
|Rated residual current breaking capacity(KA)||4.5|
|Mechanical & electrical life:||20,000 operations|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm², Cross-section of busbar from 0.8-2mm²,reversibility of connections|
|Tightening torque||2 Nm|
|Ambient temperature (°C)||- 5°C ~ +40°C|
|Relative air humidity||no more than 95%|
|Installation condition||Used in place without obvious shock and vibration|
|Weight (g)||340 420 530 630 710|
Exterior and dimensions
|Number of poles||Width（mm）||Modules|
|1 / 2||54||3|
|2 / 2||72||4|
|3 / 3||100||5.5|
|3 / 4||112.5||6.25|
|4 / 4||130.5||7.25|
testing how my 6 AMP circuit breaker would work with a microwave oven transformer,turns out it will work fine until the MOT secondary is completely shorted out so this seems a good setup for my purpose.
Relay vs Circuit Breaker- Difference between Relay and Circuit Breaker
The difference between the Relay and Circuit breaker is explained on the various factors like the principle of their operation, working of relay and circuit breaker, type of device they are, voltage, their usability and whether it works as an amplifier or not.
In this video we will go to learn Difference between Relay and Circuit Breaker.
MCCB vs MCB│ Difference between MCCB and MCB│
ELCB vs RCCB │ Difference Between ELCB and RCCB│
Thanks for watching this video. Don’t forget like share and comments. More update please subscribe our channel learning Engineering.
content source by-