Factory best selling Miniature circuit breaker-FTB2LE for El Salvador Manufacturers
Exterior and dimensions
We have our own sales team, design team, technical team, QC team and package team. We have strict quality control procedures for each process. Also, all of our workers are experienced in printing field for Factory best selling Miniature circuit breaker-FTB2LE for El Salvador Manufacturers, Adhering to the business principle of mutual benefits, we have won good reputation among our customers because of our perfect services, quality products and competitive prices. We warmly welcome customers from home and abroad to cooperate with us for common success.
|Model||FTB2LE Miniature circuit-breaker|
|Number of poles||IP+N,2P,3P,3P+N,4P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V) AC||230/400|
|Rated current (A)||C
|6, 10, 16, 20, 25, 32, 40, 50, 63
|Rated residual operating current(mA)||AC A||30
|Rated residual non-operating current(mA)||AC
|Residual current breaking time||30mA≦0.1s 250mA≦0.04s|
|Max. breaking time(s)||0.1|
|Rated short-circuit breaking capacity(KA)||6.5|
|Rated residual current breaking capacity(KA)||4.5|
|Mechanical & electrical life:||20,000 operations|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm², Cross-section of busbar from 0.8-2mm²,reversibility of connections|
|Tightening torque||2 Nm|
|Ambient temperature (°C)||- 5°C ~ +40°C|
|Relative air humidity||no more than 95%|
|Installation condition||Used in place without obvious shock and vibration|
|Weight (g)||340 420 530 630 710|
Exterior and dimensions
|Number of poles||Width（mm）||Modules|
|1 / 2||54||3|
|2 / 2||72||4|
|3 / 3||100||5.5|
|3 / 4||112.5||6.25|
|4 / 4||130.5||7.25|
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/FAP34030,22-10150.aspx
Stock # 22-10150, SQUARE D, Circuit Breaker, Catalog No. FAP34030, Frame Amps 100, Trip Amps 30, 3 Poles, 480 Volts,
Reconditioned Circuit Breakers
The FAP34030 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The FAP34030 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the FAP34030. These services far exceed the routine reconditioning of the FAP34030 performed by many circuit breaker vendors and resellers. MIDWEST certifies the FAP34030 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the FAP34030 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus FAP34030 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus FAP34030 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209
Customer reported chilled drinks case over temperature and the breaker tripped for the condensing unit.
Tested and found the compressor shorted to ground, ordered a new one for next day delivery and fitted along with a new contactor and filter drier.
I also adjusted the anti cycle timer as it was set for 0.5 seconds or something equally pointless.