Factory Promotional Automatic Transfer Switching Equipment-FTQ2 Wholesale to Lahore
Exterior and dimensions
Adhering to the principle of "quality, service, efficiency and growth", we have gained trusts and praises from domestic and international client for Factory Promotional Automatic Transfer Switching Equipment-FTQ2 Wholesale to Lahore, If you are interested in any of our products or would like to discuss a custom order, please feel free to contact us. We are looking forward to forming successful business relationships with new clients around the world in the near future.
|Rated operational voltage Ue(V):||AC400V/50HZ|
|Rated operational current Ie(A):||20,25,32,40,50,63,80,100,125,160,180,200,225,315,350,400,500,630|
|Rated insulation voltage Ui(V):||690V|
|Operating position:||Normal power switch-on, backup power switch-on, Normal power& backup power switch-off|
|Rated controller Operating supply voltage:||AC220V|
|Under-voltage:||Adjustable from 160-200v,factory defaults:170V|
|Over-voltage:||Adjustable from 240-290V,factory defaults:270V|
|Operation Mode:||R:automatic change recovery,S:automatic change but not automatic recovery,F:Generator type|
|Switch-off delay time:||Adjustable from 0-180s,factory defaults:2s|
|Switch-on delay time:||Adjustable from 0-180s,factory defaults:2s|
Relay vs Circuit Breaker- Difference between Relay and Circuit Breaker
The difference between the Relay and Circuit breaker is explained on the various factors like the principle of their operation, working of relay and circuit breaker, type of device they are, voltage, their usability and whether it works as an amplifier or not.
In this video we will go to learn Difference between Relay and Circuit Breaker.
MCCB vs MCB│ Difference between MCCB and MCB│
ELCB vs RCCB │ Difference Between ELCB and RCCB│
Thanks for watching this video. Don’t forget like share and comments. More update please subscribe our channel learning Engineering.
content source by-