Factory Wholesale PriceList for DC miniature circuit breaker-FTBD for Danish Factory
Exterior and dimensions
We aim to find out quality disfigurement from the production and supply the best service to domestic and overseas customers wholeheartedly for Factory Wholesale PriceList for DC miniature circuit breaker-FTBD for Danish Factory, We warmly welcome all perspective inquiries from home and abroad to cooperate with us, and look forward to your correspondence.
|Model||FTBD DC miniature circuit-breaker|
|Number of poles||IP||2P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V)||125/250||250/500|
|Rated current (A)||1,2,3,4|
|Rated ultimate short-circuit breaking capacity(KA)||6.5|
|Rated current (A)||6,10,16,20,25,32,40,50,63|
|Rated ultimate short-circuit breaking capacity(KA)||20/10||20/10|
|Rated impulse withstand voltage Uimp(KV)||4|
|Mechanical and electrical life:||20000|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm2, Cross-section of busbar from 0.8-2mm2|
|Ambient temperature (°C)||-25°C ~ +45°|
|Relative air humidity||no more than 95%|
|Installation condition||Used in place without obvious shock and vibration|
Exterior and dimensions
|Number of poles||1P 2P|
Vídeo descritivo do Módulo Isolador MIE G3 da Microsol.
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/THED136060,22-12427.aspx
Stock # 22-12427, GENERAL ELECTRIC, Circuit Breaker, Catalog No. THED136060, Frame Amps 150, Trip Amps 60, 3 Poles, 600 Volts,
Reconditioned Circuit Breakers
The THED136060 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The THED136060 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the THED136060. These services far exceed the routine reconditioning of the THED136060 performed by many circuit breaker vendors and resellers. MIDWEST certifies the THED136060 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the THED136060 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus THED136060 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus THED136060 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209