Factory Wholesale PriceList for Moulded Case Circuit Breaker-FTM2 for Korea Manufacturers
Exterior and dimensions
Our well-equipped facilities and excellent quality control throughout all stages of production enables us to guarantee total customer satisfaction for Factory Wholesale PriceList for Moulded Case Circuit Breaker-FTM2 for Korea Manufacturers, We are confident to make great achievements in the future. We are looking forward to becoming one of your most reliable suppliers.
THIS VIDEO ABOUT OF MCB AND MCB WIRING CONNECTION please see this video & learn mcb wiring connection.
MCB connection or wiring of mcb Circuit breaker of single pole, double pole , three pole and four pole in Urdu & Hindi.
A complete guide of single pole or one pole MCB (miniature circuit breaker) Wiring guide in Urdu / Hindi. This video help electrical students to learn electrical .
This video about of 2 pole mcb wiring connection, and 2 pole mcb installation ये वीडियो दो पोल की मिनीयेचर सर्किट ब्रेकर.
Disclaimer: This video is to show the way I did the job of upgrading my 10/3 feeder wire. I am not showing the way all the experts watching would do it. I am a licensed aircraft avionics (electrician) not a home electrician:I did not cut a long opening in the drywall. This sub-panel was inspected by an electrical underwriter back in 1985. Now I am wiring my new workshop with an existing sub-panel I had installed back in 1985. I am a licensed aircraft technician and was allowed by the town code board to wire my own one family house wiring, including connecting to the incoming power company wiring that terminated on a pole connected to my house, this was back in 1985, I do not think that is allowed anymore.Now I am updating the size to 10/3 coming from the sub-panel to the underground UV cable I had buried back in 1985. The two 30 amp switches I have been using, although renewed, could be eliminated and just use the sub panel circuit breakers when your not using shed power, also I am installing an 8 foot copper rod, pounded into the ground and connected to the shed box neutral bar using unshielded solid # 4 copper wire with the required rod clamp. The main house neutral bar is also connected to a #4 solid copper ground wire unbroken to the pipe below the house’s main water shut off valve and continues out of the house and connected to an 8 foot copper rod with heavy required clamp.This gets pounded below the dirt close to the foundation. Over 616 HD Video