Fast delivery for Miniature Circuit Breaker FTB1 Wholesale to Zimbabwe
Exterior and dimensions
We always think and practice corresponding to the change of circumstance, and grow up. We aim at the achievement of a richer mind and body and the living for Fast delivery for Miniature Circuit Breaker FTB1 Wholesale to Zimbabwe, We welcome customers, business associations and friends from all parts of the world to contact us and seek cooperation for mutual benefits.
|Auxiliary contact||Auxiliary contact and alarm contact||Shunt release||Shunt release and auxiliary contact||Under voltage release||Over voltage release||Busbar mounting base||Motor-driven operation|
Under normal condition, the working principle of main thermostic bimetal in FTB1 SMCB is the same to the usual circuit breakers, it is used for overload tripping. when there is a short-circuit on a branch circuit breaker, the magnet core in the main current path would tilt the moving contact away from the fixed contact to break the circuit,thus producing the electric arc, and limiting the short-circuit current effectively.
In the maintime,the short-circuit current flow to the supplementary current path, a selective resistor and a selective bimetal are connected in series of the supplementary curret path, limiting the short-circuit current to a few hundred amps.
When the downstream circuit-breaker has tripped because of a short-circuit, the contact tips reclose automatically through a simple spring-type system,ensuring other unaffected branch circuits continue in operation.If a short-circuit occur between the FTB1 and the downstream circuit-breaker, another bimetal release enables short-time delayed tripping,ensuring the contact tips remain in the open position enabling isolating.
Scope of use
It is primarily used in critical installations,for instance, office buiding, laboratory, theatre, museum, hotel, shopping mall, telecommunication, coal mine and shipping, chemical industry and metallurgy, industrial plants,medical and health care, bank and securities exchange,airport, underground express way, military establishment and similar loads that requires non-interrupted and reliable power supply.
|Test||Tripping characteristic||Conventional non-tripping current||Conventional tripping current||Initial status||Tripping time|
|a b||E E||1.05In||1.2In||Cold statusRight after test 1||≧2h﹤2h|
|Test||Tripping characteristic||Delayed tripping current||short-time delayed tripping current||Initial status||Tripping time|
|c||E||5In||Cold status||0.05s<t<5s(In≦32A) 0.05s<t<10s(In>32A)|
The FTB1 series operates selectively with respect to the combination with MCBs
|MCB(B,C characteristic) FTB1(Characteristic E)|
Note: T represents total selectivity
Exterior and dimensions
http://www.electrical-online.com Step-by-step instructions on how to replace a pool light. In this informative video, the Internet Electrician demonstrates the process of replacing a burnt out pool light from the pool deck. As a follow up to his first video covering pool light replacement, Terry shows you that you don’t have to take a dip in the pool in order to replace that pool light!
This is my step by step video series on how to install an off-grid stand-alone battery backup solar power system.
Here is a MidNite Solar Photovoltaic Combiner Box. This is also called a junction box, and has a Din rail allowing 6 x 15Amp breakers, so we can wire 6 “Strings” of panels.
System specs and major component parts:
48Volt Nominal System
4100Watt Solar Array (18 x 230Watt SoPray Polycrystalline Photovoltaic Solar Panels)
4400Watt 48V Magnum Pure-Sine Inverter,
Outback FM80 80Amp Charge Controller with MPPT
16 x L-16 6V Deep Cycle Batteries
Main Enclosure Panel (Custom API E-Panel)
MidNite Solar 6 String Combiner Box
ProSolar Roof Rack and Fast Jack Mounting
**Solar power arrays and components are designed to be installed by professionals. They are Dangerous electrical instruments. Misuse could result in injury or death. Please do not try this at home.