Hot sale good quality FTHN-12 (XGN15-12) Metal Closed Box ing High Voltage Switchgear Supply to Monaco
Exterior and dimensions
Gaining customer satisfaction is our company's aim forever. We will make great efforts to develop new and top-quality products, meet your special requirements and provide you with pre-sale, on-sale and after-sale services for Hot sale good quality FTHN-12 (XGN15-12) Metal Closed Box ing High Voltage Switchgear Supply to Monaco, Create Values,Serving Customer!" is the aim we pursue. We sincerely hope that all customers will establish long term and mutually beneficial cooperation with us.If you wish to get more details about our company, Please contact with us now.
FTHN-12 Indoor exchange metal closed box ring high voltage switchgear is Complete sets of power distribution equipment with 3.6 ~ 12Kv, three-phase, AC 50Hz. It is widely used in the power distribution system of construction and transformation of urban power grids also used in the power supply system of the industrial and mining enterprises, high-rise buildings, residential quarters, hospitals, schools, parks etc for the use of the power acceptance and distribution.
Mainly used for ring network power supply system, for the use of power acceptance and distribution.
Mainly used for ring network power supply and terminal power supply, also suitable for installing into the assembly substation.
This product complies with GB3804-1990, GB3906-2006, GB16926-1997, GB / T11022-1999, GB15166.2-1994, GB1985-1989, GB3309-1989, IEC420-1990 and other standards, and passed all type of test.
Operating environmental conditions
A) Ambient temperature
Maximum temperature: + 40 ℃
Minimum temperature: -15 ℃
Daily average: ≤35 ℃
B) Ambient humidity
Daily average relative humidity: ≤ 95%
Monthly average relative humidity: ≤90%
Daily average vapor pressure: ≤2.2X10-3 Mpa
C) Altitude: no more than 1000m;
D) earthquake intensity does not exceed 8 degrees;
E) Operating place without water dripping, no flammable and explosive hazards, no chemical corrosion of gas and no severe vibration.
If your portable generator runs but doesn’t produce output voltage, you can use a corded drill to reintroduce the residual magnetism the alternator needs to produce electricity. This video shows you how.
In this video I explain how to choose an Uninterruptable Power Supply (UPS) to protect your computer and other electronically sensitive devices from damage due to storms or neighbors who like to play with circuit breakers. I go over what to plug into and what to avoid plugging into an UPS. Additionally I use a web calculator that is designed to assist people in choosing the correct UPS based on the equipment’s power requirement.
My Site: http://www.bucketofmass.com
APC product selector: http://www.apc.com/tools/ups_selector/
Tripp Lite product selector: http://www.tripplite.com/en/products/selectors/ups/index.cfm