Low price for Miniature circuit breaker-FTB10 Wholesale to Surabaya
Exterior and dimensions
"Control the quality by the details, show the strength by quality". Our company has strived to establish a highly efficient and stable staff team and explored an effective quality control process for Low price for
Miniature circuit breaker-FTB10 Wholesale to Surabaya, we are now looking forward to even greater cooperation with overseas customers based on mutual benefits. If you are interested in any of our products, please feel free to contact us for more details.
|Rated current (A):||6,10,16,20,25,32,40|
|Rated voltage (V):||230|
|Rated impulse withstand voltage Uimp(KV):||4|
|Operating cycle times||/hour||240|
|Conventional non-tripping current:||1.13In||t≤1h|
|Instantaneous tripping type:||C|
|Instantaneous non-tripping current:||t≤0.1s||5In|
|Instantaneous tripping current:||t<0.1s||10In|
|Connection Wire ㎜²:||Min/Max||1/10|
In this video, we walk you through the steps to perform a conventional circuit breaker timing test with the Vanguard CT-7000 S3 circuit breaker analyzer.
To learn more about Vanguard’s comprehensive line of testing instruments, visit us at http://www.vanguard-instruments.com.
we had added three 33KV GIS switchgears to existing switchgear panels , as part from testing , we intended to conduct high voltage test .
As per Saudi Electricity company , we have to apply 57KV for a period of 1 minuet (Power Frequency withstand) .
we started increasing the voltage gradually till we reached 50KV were a flash over happened as shown in the video .
Any suggestion for this issue?
Jeddah , Saudi Arabia