New Delivery for Automatic Transfer Switching Equipment-FTQ2E for Sacramento Manufacturer
Exterior and dimensions
Dedicated to strict quality control and thoughtful customer service, our experienced staff members are always available to discuss your requirements and ensure full customer satisfaction for New Delivery for Automatic Transfer Switching Equipment-FTQ2E for Sacramento Manufacturer, Inspired by the rapid developing market of the fast food and beverage consumables all over the world , We are looking forward to working with partners /clients to make success together .
|Body switch||FTB2-63 MCB Series|
|Rated voltage (V)：||AC 400(4P/3P); AC 230V(2P)/50HZ|
|Rated insulation voltage:||440|
|Rated impulse withstand voltage Uimp(KV):||4|
|Rated breaking Capacity：||6.5|
|Mechanical and electrical life:||electric||6000|
|Operating position:||Normally on,backup on,Normal and backup off|
|Operating transfer time:||≤1.5|
switch automaticly in condition of phase loss, pressure loss ,undervoltage and other power failure,
automatic change and automatic recovery ,automatic change and non automatic recovery,fire fighting
joint control, Manual/automatic adjustion,power/power on/tripping indication,fault alarm
|Controller Operating Voltage:||AC230V/50Hz|
|Undervoltage conversion value:||AC175V(±5)|
|Undervoltage return value:||AC190V(±5)|
|Conversion Delay(normal to backup):||0S-60S adjustable,factory default setting:5S|
|Return Delay（normal to backup:||0S-60S adjustable,factory default setting:5S|
|Size（L×W×H）mm:||248 × 125×121|
Shed Electric Installation
Cost was about $500.
10/3 w/ground NM Cable runs from DP 30a breaker in panel, under crawlspace to outdoor box. Transitions to 4 separate conductors of THWN, 10 gauge (H1, H2, N, G)
18″ Deep 3/4″ PVC conduit
1 ground rod 8ft long in ground, fed with #6 ground wire as per local code. If water was fed into the building from the house well/plumbing, 2 would be required located 6 ft apart.
Up into the subpanel, where it is wired up with 14/2 NM cable using 15 amp breakers. Many circuits were added since these are where the interior/exterior lights are also controlled/turned on/off. This lets me lock the subpanel when I have company so no one plays with the lights or breakers, via a cam lock I still have to install on the panel door.