OEM/ODM Factory for Air Circuit Breaker-FTW1 to London Manufacturer
Exterior and dimensions
Our development depends on the advanced equipment ,excellent talents and continuously strengthened technology forces for OEM/ODM Factory for Air Circuit Breaker-FTW1 to London Manufacturer, Any requires from you will be paid with our best attention!
Disclaimer: This video is to show the way I did the job of upgrading my 10/3 feeder wire. I am not showing the way all the experts watching would do it. I am a licensed aircraft avionics (electrician) not a home electrician:I did not cut a long opening in the drywall. This sub-panel was inspected by an electrical underwriter back in 1985. Now I am wiring my new workshop with an existing sub-panel I had installed back in 1985. I am a licensed aircraft technician and was allowed by the town code board to wire my own one family house wiring, including connecting to the incoming power company wiring that terminated on a pole connected to my house, this was back in 1985, I do not think that is allowed anymore.Now I am updating the size to 10/3 coming from the sub-panel to the underground UV cable I had buried back in 1985. The two 30 amp switches I have been using, although renewed, could be eliminated and just use the sub panel circuit breakers when your not using shed power, also I am installing an 8 foot copper rod, pounded into the ground and connected to the shed box neutral bar using unshielded solid # 4 copper wire with the required rod clamp. The main house neutral bar is also connected to a #4 solid copper ground wire unbroken to the pipe below the house’s main water shut off valve and continues out of the house and connected to an 8 foot copper rod with heavy required clamp.This gets pounded below the dirt close to the foundation. Over 616 HD Video