OEM/ODM Manufacturer FTKN (KYN28A) -12 Indoor Exchange Metal Armored Withdrawable Switchgear for Burundi Factory
Exterior and dimensions
To meet the customers' over-expected satisfaction , we have our strong team to provide our best overall service which includes marketing, sales, designing, production, quality controlling, packing, warehousing and logistics for OEM/ODM Manufacturer
FTKN (KYN28A) -12 Indoor Exchange Metal Armored Withdrawable Switchgear for Burundi Factory, we are now looking forward to even greater cooperation with overseas customers based on mutual benefits. If you are interested in any of our products, please feel free to contact us for more details.
FTKN (KYN28A) -12 indoor exchange metal armored withdrawable switchgear is the transmission and distribution control of the single bus segmentation system device that is used for receiving and distributing the power.
It is mainly used for power distribution of power plants, small and medium-sized generator transmission, industrial and mining enterprises and also used for accepting and feeding, large high voltage motor starting plants of the secondary substation to control, protect and detect the whole line.
Relay vs Circuit Breaker- Difference between Relay and Circuit Breaker
The difference between the Relay and Circuit breaker is explained on the various factors like the principle of their operation, working of relay and circuit breaker, type of device they are, voltage, their usability and whether it works as an amplifier or not.
In this video we will go to learn Difference between Relay and Circuit Breaker.
MCCB vs MCB│ Difference between MCCB and MCB│
ELCB vs RCCB │ Difference Between ELCB and RCCB│
Thanks for watching this video. Don’t forget like share and comments. More update please subscribe our channel learning Engineering.
content source by-
UPS failed while I was checking the batteries after the vendor finished battery maintenance. This was my last walk-through of the day. I checked the battery voltage and current at the UPS panel, inspected each battery for signs of leakage or post swelling. I was going to print a battery report when I noticed the battery monitor printer was near the end of the paper. I looked for a new roll of paper and just as I closed the door, the UPS failed releasing a fireball into the room. The failure tripped one of the three 3000 AMP main feeders, the battery breaker and the UPS input breaker. My first concern was all the smoke even though the fire sensors in this room are heat detecters. By the time I got the door open to vent the smoke and add light to the room, my phone was blowing up with alarms. Though I was quite busy for the next few hours, none of the computers in the center were affected.
I learned that the failure in the UPS was a phase-to-phase short on the input 480 VAC circuit, apparently through the diodes or SCRs in the input AC side.