Ordinary Discount Automatic Transfer Switching Equipment-FTQ2 Export to Cape Town
Exterior and dimensions
We strive for excellence, service the customers", hopes to become the best cooperation team and dominator enterprise for personnel, suppliers and customers, realizes value share and continuous promotion for Ordinary Discount Automatic Transfer Switching Equipment-FTQ2 Export to Cape Town, We sincerely welcome you come to visit us. Hope we have good cooperation in the future.
|Rated operational voltage Ue(V):||AC400V/50HZ|
|Rated operational current Ie(A):||20,25,32,40,50,63,80,100,125,160,180,200,225,315,350,400,500,630|
|Rated insulation voltage Ui(V):||690V|
|Operating position:||Normal power switch-on, backup power switch-on, Normal power& backup power switch-off|
|Rated controller Operating supply voltage:||AC220V|
|Under-voltage:||Adjustable from 160-200v,factory defaults:170V|
|Over-voltage:||Adjustable from 240-290V,factory defaults:270V|
|Operation Mode:||R:automatic change recovery,S:automatic change but not automatic recovery,F:Generator type|
|Switch-off delay time:||Adjustable from 0-180s,factory defaults:2s|
|Switch-on delay time:||Adjustable from 0-180s,factory defaults:2s|
When it comes to overcurrent protection… I prefer a fuse than a circuit Breaker as they are more reliable.
I also hate cheaply made stuff. Cheap USB chargers urk me. If it results in poorly designed circuits… I want nothing to do with them.!
One Man shows you how to install a new breaker.