PriceList for Miniature Circuit Breaker FTB1 for Anguilla Importers
Exterior and dimensions
Our target is to consolidate and improve the quality and service of existing products, meanwhile constantly develop new products to meet different customers' demands for PriceList for Miniature Circuit Breaker FTB1 for Anguilla Importers, We warmly welcome your participation based on mutual benefits in the near future.
|Auxiliary contact||Auxiliary contact and alarm contact||Shunt release||Shunt release and auxiliary contact||Under voltage release||Over voltage release||Busbar mounting base||Motor-driven operation|
Under normal condition, the working principle of main thermostic bimetal in FTB1 SMCB is the same to the usual circuit breakers, it is used for overload tripping. when there is a short-circuit on a branch circuit breaker, the magnet core in the main current path would tilt the moving contact away from the fixed contact to break the circuit,thus producing the electric arc, and limiting the short-circuit current effectively.
In the maintime,the short-circuit current flow to the supplementary current path, a selective resistor and a selective bimetal are connected in series of the supplementary curret path, limiting the short-circuit current to a few hundred amps.
When the downstream circuit-breaker has tripped because of a short-circuit, the contact tips reclose automatically through a simple spring-type system,ensuring other unaffected branch circuits continue in operation.If a short-circuit occur between the FTB1 and the downstream circuit-breaker, another bimetal release enables short-time delayed tripping,ensuring the contact tips remain in the open position enabling isolating.
Scope of use
It is primarily used in critical installations,for instance, office buiding, laboratory, theatre, museum, hotel, shopping mall, telecommunication, coal mine and shipping, chemical industry and metallurgy, industrial plants,medical and health care, bank and securities exchange,airport, underground express way, military establishment and similar loads that requires non-interrupted and reliable power supply.
|Test||Tripping characteristic||Conventional non-tripping current||Conventional tripping current||Initial status||Tripping time|
|a b||E E||1.05In||1.2In||Cold statusRight after test 1||≧2h﹤2h|
|Test||Tripping characteristic||Delayed tripping current||short-time delayed tripping current||Initial status||Tripping time|
|c||E||5In||Cold status||0.05s<t<5s(In≦32A) 0.05s<t<10s(In>32A)|
The FTB1 series operates selectively with respect to the combination with MCBs
|MCB(B,C characteristic) FTB1(Characteristic E)|
Note: T represents total selectivity
Exterior and dimensions
Replacing an e-bike battery pack or electric scooter battery pack can be easy if you take your time and follow a system. MobilityUnlimited is pleased to offer this free demonstration for those wish to do it themselves and save some money. It can also be dangerous if you drop metal that connects a Positive and Negative connection. Be careful. Produced and supported by SeveralArts Ventures Inc.
This video will step you through every function of the new VDV II Pro cable tester from IDEAL Industries. Ron walks you through how to use the tester to test coaxial, phone and data cabling like Cat 5e/6/6A. Grab your favorite drink it is about 44 minutes long.