PriceList for Miniature circuit breaker-FTG11 to Croatia Manufacturer
Exterior and dimensions
With the "Client-Oriented" business philosophy, a rigorous quality control system, advanced manufacturing equipment and a strong R&D team, we always provide high quality products, excellent services and competitive prices for PriceList for Miniature circuit breaker-FTG11 to Croatia Manufacturer, "Create Values,Serving Customer!" is the aim we pursue. We sincerely hope that all customers will establish long term and mutually beneficial cooperation with us.If you wish to get more details about our company, Please contact with us now
|Rated current (A):||32,63,100|
|Rated operational voltage||400|
|Rated insulation voltage:||690|
|Rated short-time connecting capacity||conduction time:0.1s||30Ie|
|Rated short-time withstand current||conduction time:1s||20Ie|
|Rated connecting and breaking capacity||3Ie|
|Rated impulse withstand voltage Uimp(KV):||4|
A few tests and observations for the research currently being conducted over on this thread: http://www.energeticforum.com/renewable-energy/8801-magnet-kicker-thread.html
The 10 strand coil information can be found in the Muller Generator thread on the same messageboard.
The base circuit can be found on mariuscivic’s video of his Magnet Kicker original build.
What causes a circuit breaker to trip
Power Bars and Surge Protectors are the main culprits
As handy and convenient as they are they are the most likely cause of a circuit being over loaded and therefore drawing too much current. More current than what the wires are physically capable of handling which is why there is a circuit breaker to prevent overloading which in turn prevents overheating of the wires inside the walls.
Think about it…if those wires were allowed to get too hot they would combust inside the walls.