professional factory for Miniature circuit breaker-FTM8-LE to Russia Manufacturer
Exterior and dimensions
We have many excellent staff members good at marketing, QC, and dealing with kinds of troublesome problem in the production process for professional factory for Miniature circuit breaker-FTM8-LE to Russia Manufacturer, Our professional technical team will be wholeheartedly at your service. We sincerely welcome you to visit our website and company and send us your inquiry.
|Model||FTM8LE Residual current circuit-breaker|
|Number of poles||IP+N,2P,3P,3P+N,4P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V) AC||230/400|
|Rated current (A)||C D||1,3,6,10,16,20,25,32,40,50,63 1,3,6,10,16,20,25,32,40,50,63|
|Rated residual operating current(mA)||30|
|Rated residual non-operating current(mA)||15|
|Residual current breaking time||30mA≦0.1s 250mA≦0.04s|
|Rated short-circuit breaking capacity(KA)||6(In≦40A); 4.5(In﹥40A)|
|Rated residual current breaking capacity(KA)||3|
|Mechanical & electrical life:||10,000 operations|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm2|
|Tightening torque||2 Nm|
|Ambient temperature (°C)||-5°C ~ +40°C|
|Relative air humidity||no more than 95%|
|installation condition||Used in place without obvious shock and vibration|
Exterior and dimensions
|Number of poles||Rated current|
I was hired to replace an old electrical service panel but the meter was locked on. This is highly dangerous and should only be done by a licensed professional. Proceed at YOUR OWN RISK. Do not steal power, it’s against the law! Please comment, like or dislike and feel free to ask any questions. I don’t mind helping!
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/EHC3015,22-14444.aspx
Stock # 22-14444, CUTLER HAMMER, Circuit Breaker, Catalog No. EHC3015, Frame Amps 150, Trip Amps 15, 3 Poles, 480 Volts
Reconditioned Circuit Breakers
The EHC3015 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The EHC3015 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the EHC3015. These services far exceed the routine reconditioning of the EHC3015 performed by many circuit breaker vendors and resellers. MIDWEST certifies the EHC3015 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the EHC3015 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus EHC3015 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus EHC3015 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209