Renewable Design for MNS Low Voltage Withdrawable Switchgear for Qatar Factory
Exterior and dimensions
Our company sticks to the principle of "Quality is the life of the company, and reputation is the soul of it" for Renewable Design for MNS Low Voltage Withdrawable Switchgear for Qatar Factory, We invites you and your enterprise to thrive together with us and share a bright future in global market.
MNS low-voltage withdrawable switchgear is suitable in three-phase, four-wire and three-phase five-wire power system with three-phase AC 50 or 60 Hz, rated voltage 660V, rated current ≤ 4000A , for the use of electricity power acceptance and distribution. It is widely used in power plants, substations, factories, mines, high-rise buildings of the power distribution center PC and motor control center MCC.
This product complies with GB7251.1-91, ZBK36001-89, IEC439-1 (1992) standard and passed CCC certificate:
To purchase, visit:http://www.swgr.com/store/circuit-breakers/molded-case/product/EHC3100,22-14449.aspx
Stock # 22-14449, CUTLER HAMMER, Circuit Breaker, Catalog No. EHC3100, Frame Amps 150, Trip Amps 100, 3 Poles, 480 Volts,
Reconditioned Circuit Breakers
The EHC3100 Circuit Breaker has been reconditioned per MIDWEST’s rigorous service procedures based on 30 years experience. The EHC3100 circuit breaker has been maintained and refurbished per industry standards and per MIDWEST’s Quality Control Program (QCP). The services include applicable internal and external procedures, repairs, and replacement of deficient components. In addition to standard electrical tests, MIDWEST also performs live function tests on the EHC3100. These services far exceed the routine reconditioning of the EHC3100 performed by many circuit breaker vendors and resellers. MIDWEST certifies the EHC3100 circuit breaker has passed our QCP before shipping.
New Surplus Circuit Breakers
A “New Surplus” Circuit Breaker is a circuit breaker that has never been installed, but is not “New from the Factory” or “New from the Manufacturer or Distributor” of the EHC3100 circuit breaker. It may be referred to as New in the Box, New Surplus, Never Installed, Never Energized, or other such term that avoids the label “New from the Manufacturer.” A New Surplus EHC3100 circuit breaker should not be considered new from the manufacturer or manufacturer’s Distributor. Surplus and New Surplus EHC3100 circuit breakers must pass MIDWEST’s (QCP) Quality Control Program.
MIDWEST Electrical Testing & Maintenance Co., Inc.
5141 North 35th Street, Milwaukee, WI 53209