Wholesale Dealers of DC miniature circuit breaker-FTBD Wholesale to Turkey
Exterior and dimensions
Quality First,and Customer Supreme is our guideline to provide the best service to our customers.Nowadays, we are trying our best to become one of the best exporters in our field to meet customers more need for Wholesale Dealers of DC miniature circuit breaker-FTBD Wholesale to Turkey, sincerely look forward to serving you in the near future. You are sincerely welcome to visit our company to talk business face to face with each other and establish long-term co-operation with us!
|Model||FTBD DC miniature circuit-breaker|
|Number of poles||IP||2P|
|Rated frequency:||AC 50/60Hz|
|Rated voltage (V)||125/250||250/500|
|Rated current (A)||1,2,3,4|
|Rated ultimate short-circuit breaking capacity(KA)||6.5|
|Rated current (A)||6,10,16,20,25,32,40,50,63|
|Rated ultimate short-circuit breaking capacity(KA)||20/10||20/10|
|Rated impulse withstand voltage Uimp(KV)||4|
|Mechanical and electrical life:||20000|
|Installation||On DIN rail 35mm according to JB6525|
|Connection capacity:||Cross-section of conductors up to 25mm2, Cross-section of busbar from 0.8-2mm2|
|Ambient temperature (°C)||-25°C ~ +45°|
|Relative air humidity||no more than 95%|
|Installation condition||Used in place without obvious shock and vibration|
Exterior and dimensions
|Number of poles||1P 2P|
o The ELB(Earth Leakage Breaker) is also called as RCD(Residual Current Device) and GFCI(Ground Fault Circuit Interrupter).
The inverters, which are widely used in washers, air conditioners, elevators etc due to their energy efficiency and detail control function, cause a lot of harmonics leakage current. This leakage current may flow through the wires of the building and thus cause malfunction to the connected appliances.
In the control rooms of factories, substations, IDC center powered from UPS, a large amount of leakage current is released and most of the time, the conventional leakage breaker(Io ELB) cannot handle the leakage and thus malfunction. Therefore, in most control rooms the leakage breaker(Io ELB) is either taken away or even never installed from the beginning, thus install MCCB instead of ELB. This is a very dangerous situation as resistive leakage current can lead to fire in these facilities.
The earth leakage breakers(ELB) operates based on Io(I zero), and therefore in the digital world of today, the breakers does not function properly in world-wide.
Therefore, our company has developed an IGR leakage breaker which can operate at the amount of resistive leakage current properly, but will not operate at capacitive leakage current properly. The innovative IGR breaker will operate more sensitively to effective factor of resistive leakage current than to non-effective factor of capacitive leakage current.
This is the IGR RCD(ELCB) specification explanation made by Korea.
IGR 누전차단기 규격 설명